Fitting New Condo Safety Issues and defects into the Top 10 list is going to be a little tight, but you can find out about many other bad things from the Chicago condos by checking entire Chicago Condo Inspection Manual. You would think that after such a spectacular real estate meltdown, something would change in … Read more
New Water Heater Installation in a Condominium – Chicago Inspection Tips
To start your inspection of a new water heater installation in a Chicago condominium you have to determine what type of a water heater you actually have.
The following water heater installation guidelines will most likely apply in any jurisdiction (please double check). The only difference or rather an addition would be water heater strapping and flexible gas connectors that are required in seismic areas.
Below are 4 most common types of water heater installation in Chicago new condos:
Tank type /natural draft water heater with a metal vent pipe (galvanized steel – make sure there is no aluminum […]
This chapter of the Chicago new condo inspection covers most common furnace installation issues (based on my inspections). Furnace air return port must be located at least 10’ from the combustion chamber(s) (where the burners are) of gas burning appliances or in a separate room. The exception from this requirement is when the furnace and other appliances (within that room and 10′) are using combustion air from the outside.
Even if you know very little about Chicago history, I’m sure you have heard of the Great Chicago Fire that started on October 8, 1871 … maybe you didn’t remember the date … This chapter of your Chicago new condo inspection covers firewall separation between the condominium units, and it will tell us if we … Read more
This part will cover Chicago condo inspection combustion air requirements for the gas furnace and water heater installed inside your condo closet / utility room (not in the building common areas) – this is an extremely important section and you may need measuring tape.
All gas burning appliances require oxygen for a proper, complete and safe combustion process / without creating measurable and dangerous amounts of Carbon Monoxide.
Because Carbon Monoxide has no taste, smell or color you must have a CO detector installed in your condo to alert you about any unsafe levels (check Chicago smoke and Carbon Monoxide detector requirements).