Kitchen GFCI receptacle
Kitchen GFCI receptacles are required by the 2008 NEC (National Electrical Code) to be installed along the countertop surfaces.
GFCI – (Ground Fault Circuit Interrupter)
Actually, this requirement has been in place since 1996 NEC, and an important thing to remember:
If you have an older kitchen, and for any reason decided to replace a regular electrical outlet – you should have a GFCI receptacle installed as a replacement.
Kitchen Electrical Requirements
Kitchen electrical outlets installed above the countertops require at least 2 small appliance branch circuits.
Kitchen electrical circuits serving countertop outlets must be rated for 20 ampers (#12 wire)
Kitchen GFCI receptacles installed [...]
Bathroom GFCI receptacle protection is required by the NEC (National Electrical Code), and of course by the common sense – why would you risk getting electrocuted if you can secure your safety by installing GFCI outlet.
Since some bathrooms are currently equipped with many electrical current hungry devices, power supply requirements had to be slightly adjusted. We used to have a bathroom sharing an electrical circuit with exterior outlets, the kitchen, and a garage – not anymore.
Of course, the minimum requirement listed below is not going to work if you add a steam shower, heated electric floor, hydro-spa heater, several light [...]