New Water Heater Installation in a Condominium – Chicago Inspection Tips
To start your inspection of a new water heater installation in a Chicago condominium you have to determine what type of a water heater you actually have.
The following water heater installation guidelines will most likely apply in any jurisdiction (please double check). The only difference or rather an addition would be water heater strapping and flexible gas connectors that are required in seismic areas.
Below are 4 most common types of water heater installation in Chicago new condos:
Tank type /natural draft water heater with a metal vent pipe (galvanized steel – make sure there is no aluminum […]
This chapter of the Chicago new condo inspection covers most common furnace installation issues (based on my inspections). Furnace air return port must be located at least 10’ from the combustion chamber(s) (where the burners are) of gas burning appliances or in a separate room. The exception from this requirement is when the furnace and other appliances (within that room and 10′) are using combustion air from the outside.
This part will cover Chicago condo inspection combustion air requirements for the gas furnace and water heater installed inside your condo closet / utility room (not in the building common areas) – this is an extremely important section and you may need measuring tape.
All gas burning appliances require oxygen for a proper, complete and safe combustion process / without creating measurable and dangerous amounts of Carbon Monoxide.
Because Carbon Monoxide has no taste, smell or color you must have a CO detector installed in your condo to alert you about any unsafe levels (check Chicago smoke and Carbon Monoxide detector requirements).
The following kitchen inspection guidelines can be used by a home inspector to establish routine procedures while performing a general home kitchen inspection. Every home owner/ seller / buyer can also follow this kitchen inspection manual to determine if his kitchen conforms to the residential construction industry standards or / and if the contractor did his job right on a brand new kitchen.
Keep in mind that building codes are updated / changed periodically and requirements my slightly vary between jurisdictions. Don’t hesitate to ask me questions and always verify if particular requirement has been adopted and is being enforced in your area by contacting your local building department.
All bathroom outlets must be 20 amps rated and must include GFCI protection (there might be one GFCI receptacle and other outlets connected to it and protected). Your new condo bathroom receptacles must be installed on #12 AWG wire which you can’t see without removing of the receptacle or at least its cover, but this is beyond our basic / visual inspection.
Requirements for the smoke and Carbon Monoxide detectors / alarms installation in the city of Chicago are slightly different than those from NEC (National Electrical Code). So if you’re moving from the Chicago suburbs or other states into the Windy City you’re actually going to need LESS smoke, fire and Carbon Monoxide protection.
So let’s continue your Chicago condo inspection and check for smoke and Carbon Monoxide detectors.
Pushing test button on smoke and Carbon Monoxide detectors may only confirm that unit is mechanically functional and it has power. This test does not guarantee proper response to smoke, flame and / or CO presence.