GFCI – (Ground Fault Circuit Interrupter)
Remember to always upgrade to the latest code requirement, if making any modifications of an older electrical installation (i.e. if replacing and old, regular / not GFCI type electrical outlet in the area where GFCI is currently required, make your life safer – install GFCI receptacle).
You should have a minimum of one dedicated 20-amper rated branch circuit supplying power to the laundry room outlet(s). Dedicated means that there should be no other receptacle outlets supplied by the same circuit (for ironing, switched lighting in the laundry room, or other rooms)
Laundry equipment outlet should be located within 6ft from the appliances. This is very important, so you are not going to use any extension cords for that purpose. Extension cords might have lower ratings than the appliance requirement – your washer or dryer might need more current than the extension cord can carry, which condition could overheat the cord and create a fire.
Receptacles installed in a laundry room without the sink do not require GFCI protection.
If you have a sink in a utility area, any receptacle outlet within 6ft from the sink outside edge must be GFCI protected
It doesn’t matter where the bar sink is (basement, bedroom, living room, etc.) if you have an electrical outlet within 6ft from the wet bar sink outside edge, it must be GFCI protected.
Washing machine installed in an unfinished basement area without a sink requires GFCI protection (to comply with an unfinished basement outlet GFCI protection requirement)
Search existing Q&A in Electrical Answers
This article was written by Dariusz Rudnicki
I'm a retired Illinois home inspector, founder and editor of checkthishouse.com, a blog which attracts around 2 thousand readers daily and is dedicated to answering the many questions of home owners and home buyers. Connect with me on Google+ Find me on Google+ Local